Single Pole Passive Infrared Wall Switch Occupancy Motion Sensor with UL
The passive infrared sensors work by detecting the difference between heat emitted from the human body in motion and the background space. The sensor switch can turn a load on and hold it as long as the sensor detects occupancy. After no motion is detected for the set time delay, the load turned off automatically.The sensor switch has one relay ( equal to single pole switch), also includes Ambient Light Level Sensor.
|Time Delay||15 Sec to 30 Mins|
|Light Level||30 Lux-Daylight|
|Standards & Certifications|
|Warranty||2 Year Limited|
Manual adjustable ambient light level prevents load from turning ON automatically during periods of ample natural light
. Turn Lights On/Off automatically
. Manual On/Automatic or Manual Off function
. Time delay Off setting is adjustable from 15 seconds to 30 minutes
. Adjustable sensitivity settings
. WOSS is compatible with all kinds of loads including electronic ballast
. Conforms to Califomia Title 24 Requirements
. UL/CUL Listed
1. Connect lead wires as WIRING DIAGRAM: Black lead to Hot wire, Red lead to Load wire, White lead to Neutral wire, and Green lead to Ground wire.
NOTE: DO NOT connect RED & WHITE wires on device together! It may cause short circuit!
Time Delay Knob
Default position:15 Seconds (Test mode)
Adjustable: from 15 Seconds to 30 Minutes (clockwise)
Sensor sensitivity Range Knob
Default position: Center at 65%
Adjustable: 30% (Position 1)to 100%(Position 4)
Note: Turn toward right for greater room space.
Turn toward left to avoid false alert in smaller room and nera the door way or hert source
Ambient Light Level Knob
Default position:Daylight (100% at position 4)
Adjustable Daylight to 30Lux (Counter clockwise)
Note :to avoid wasting energy by turn-on the light under daylight